Design of a new data centre at a new HQ on a brown field site of an established online gambling company with millions of customers worldwide.
Design Key Facts
|Facility Power Density||3.2kW/m2|
|Rack Power Density||8kW average
(up to 20kW)
|PUE Design Figure||<1.2|
|Resilience||N+1 M&E design with single mains supply & N+1 concurrently maintainable no break diesel rotary UPS. 2N electrical distribution|